eugeneduffy replied to the topic Make LED of switch stay on during CEN PLUS scenario in the forum Integration il y a 7 mois et 3 semaines
It is not possible to get led feedback of the state of a scenario on the 067553
You will need 2 scenarios.
Scenario 1 – Start=Light ON Only If=Empty Action=Delay 5min – Fan ON Stop=Light OFF
Scenario 2 – Start=Light OFF Only If=Fan is ON Action=Delay 10min – Fan OFF Stop=Light ON
You can turn the Philips hue on/off and select colour using the scenes in MyHome Up. These scenes can then be assigned to a wall controller
I use the 002633 DALI unit to control colour strip with 3 osram OTDALI units. You can then create colour rotation scenes with the MH202.
For a simpler solution you can just switch the DC lines for red, green and blue through an F411/4 to give 7 fixed colours. Obviously you will have no fades and limited colour options with this one but I find…En afficher davantage
You can use an app to see the feedback if you like but aalbanese has posted a CEN solution above that would probably be best for you if you only have spare scenario controller buttons available.
Yes, absolutely. I just prefer using a free relay channel (if present) because you get the feedback on the state of the block on the app or wall controller.
try using CEN start pressure.
Sorry, an actuator is a relay or a dimmer.
Do you have any relays or dimmers with no lights connected in your electrical panel?
You can use a spare actuator channel to act as a blocking flag. Put the address of this actuator into the "only if" section of your scenario in the MH202/MH200N. You can then assign this actuator to a basic controller or an app to activate and deactivate the block function with feedback on the controller or app.
If you don't have any…En afficher davantage
Did you open the IP range in the F454
Hi,Try adding the light sensor to the supervision gadget. If the sensor is in centralised mode you will be able to view the lux levels read from the sensor in the gadget.You could also try removing the light level condition to confirm the rest of the scenario is work correctly.Hope this helps.Eugene
Configure the sensor as "scenarios daylight and presence sensor" and assign an unused APL address. Then use the only if condition for lux level ranges.
Hi Tom,You have 2 options.1. configure the sensor as scenario presence and assign an unused APL address. In the MH202 sensor family use the presence sensor to trigger the scenario. (To re-trigger the scenario you need to a add the same sensor to the stop section.)2. configure the sensor as stand-alone presence and assign an APL from an unused…En afficher davantage
Thanks Anna,Great to see Nuvo control coming for it 🙂
Hi Lorenzo,Thanks for the information.Yes, the Youus gateway looks great…(just a bit expensive!!) Can the gateway operate as DMX and DALI together or do you need to choose one protocol. I have received my F459 and have a basic setup working with a Nuvo P200. My Italian is no good so the youtube tutorial is a bit tricky. I am very interested in…En afficher davantage
Hi Lorenzo,Where can I get the DMX driver from?Can the driver control the Enttec ODE DMX over Ethernet unit ?http://www.enttec.com/index.php?main_menu=Products&pn=70305ThanksEugene
Hi Richard,I removed scene 8 and this stop the light turning back on when the sensor timed out.Thanks for your help.Regards,Eugene.
Hi Jules,You can connect one of the outputs of a F411/4 to the control circuit of a relay that can switch a much higher rated load. For example you could have it switching a 4 pole 63amp contactor if you needed to!Regards Eugene.
I used imyhome to turn the light off at 20:13:14
Hi Richard,I think the above scenario was causing the light to come back on when the sensor timed out! Something not right there but I know the 002645 has some issues, maybe this is one of them?Once this scenario is removed everything works well. The scenario id for above is 8 when I look in the web pages. Can you tell me what is what 39…En afficher davantage