CompanyCentro de Iluminación Lumicentro CA
dchramcow started the topic Recommended Bticino iOS app and Server/Gateway (plus a couple more questions) in the forum Integration 4 months, 3 weeks ago
Hello MyOpen Community,
What is the current official solution for an iOS app and Server/Gateway nowadays?
Back in the day it was the MyHome BTicino app costing 50 Euros and the F454/F455 as the gateway.
Does the current solution come with an integrated DDNS service for remote access?
Thanks a lot! Have a nice day.
Thanks for the reply Lorenzo.
I got the *99*9## out of the OWN introduction document: http://oi68.tinypic.com/261kp5g.jpg
Just tried with *99*0## and it started working correctly.
One thing I wanted to ask you guys is if it was possible to disable the 30 seconds timeout it has for TCP/IP connections. If I start Putty and connect to the F455,…[Read more]
So, we just got an F455 for the office to try it out (we’ve only used F454, F452V and MH200N as gateways), we took it out of its box, made all the necessary initial configuration (pressed the button for over 20secs so it would default to DHCP, changed admin password, etc), we can access it’s web setup just fine, but when I try to send commands t…[Read more]
Thank you so much Staff.
Hello My Open Community,
I need your help with something, I can’t seem to find any of the Open Web Net guides (WHO=1, WHO=2, etc.) on this new redesigned web site.
I need to read up on how to control Bticino MyHome’s HVAC systems.
Thanks for replying Leonardo.
You are absolutely right, it was an internal unit (345020) auto answering the calls made from the entrance panel, that's why the other extensions weren't able to correctly answer a call if I waited more than ~5 secs.
Is there a way to disable the auto answer feature on these units?
In your opinion what would be the difference between a "basic" and a "big" gateway?
Would this gateway allow me to change the audio inputs of my P3100 with CEN+ commands?
What about volume control?
When you say configured in the driver, what do you mean?
How would a control a Nuvo player with CEN Plus commands?
I'm aware of that.
But can I send Open Web Net Commands to it? just like with the MH200N and F454?
Yes, both the actuator and the F452V are on the main SCS line.
Thanks for clarifying that the command is indeed correct.
The F452V must be refusing these 2 digit A-PL commands.
What would be the correct Open Web Net command for the following A PL configuration?:
I'm using a F452V.
Which works perfectly fine as a gateway, but as soon as I try to send a command with A or PL higher than 9, for example:
It's not doing anything, it gives me *#*0##.
I guess the main question for me is whether there's some extra parameters I need to add in the command for A and PL higher than 9.
I want to create something like a Panic Button.
Nevermind. Brain fart.Changed the password through MyHome Suite 3.2. Sorry guys.
dchramcow ha risposto alla discussione F411/4 and F411/2 turning on only by Group but not by Area/Light nel forum Automation 3 years, 2 months ago
Thanks for all the suggestions.It was indeed connected to the wrong side of one of the physical expansions, after changing it, it all started working properly.Thanks.
dchramcow replied to the topic Is there a way to enable a MH200N scenario from a TouchScreen (3.5 or 10 inches)? in the forum Scenario Scheduler 3 years, 2 months ago
With the use of a CEN Plus command.All I did was create a CEN Plus button on my touchscreen (with a certain ID), and on my MH200N, put that very same CEN Plus command as the trigger for my scenario. It worked perfectly.
Just out of curiosity, how did you trace these open web net commands?I'm really interested.
dchramcow replied to the topic Is there a way to enable a MH200N scenario from a TouchScreen (3.5 or 10 inches)? in the forum Scenario Scheduler 3 years, 3 months ago
After digging around this forum I have found the answer to my question.Thanks anyways.