Yes, you can. Create *two* BUS segments, every one with his own EA6ADCN, and join the segments via a F422, configuring as galvanic isolation only.
Sorry for unclear…a)"Simultaneously" refers to isolate zone with one key and later isolate other WITHOUT restore previous isolated zone.(ex, two different employees enter succesively to two zones, and go out later in different order)c) I'm referring not to includ/exclude 4606 but how keypad knows if exclude or include… togle every…[Read more]
ScenaryX works? So, your computer is in MH200N Security configuration Autorized IP range. Try using a IP for your computer OUTSIDE of authorized IP Range of MH200N. Sometimes I found strange hangs after authentication if your computer IP uses a range IP..
Instead you update time by time the MASTER system, the system must have a master… Using a OpenWebNet command you already update the master, that updates all the slaves…
So, proccessing speed frames at MH200N is strickly slow than the F453AV? I have an arduino using the gateway for open lights with a sensor, and I found a bigger delay in MH200(N)(Tested without scenarios)
"There is no master clock in the system" ???The system MUST have a master clock for MH200N. If no other master clock is set, you will set the MH200N as MASTER, not slave
When you are connected to MH200N with the webserver page, the slow speed produces LATENCY in MH200N. In Facts, when a sensor must open a light, you may found a delay of more that two seconds, because the gateway is working sending the start/stop scenary and the scenary info to the internal apache. If you have about 100 Scenarios a 100mz may be…[Read more]
non e vero il manual?http://www.catalogo.bticino.it/…/CDA00097_U4614A.pdf.. 6 – RJ 45 per lan Ethernet 10/100 MBit….
Another way is use a relatively inexpensive F420, record the blink with ScenaryX and call the F420 Scenario from MH200(N)
jaumep replied to the topic Mixing software using password and software needing an IP range on same PC still not possible? in the forum OpenWebNet 7 years, 2 months ago
Use a VMWare free client, install XP in a box, and use as an ip outsise trusted IP.I use this XP box with all BT software over a W7 host…
And Environment 0? *1*1*000## ?Light Point 0 in Environment 10? *1*1*0000## ? Tnks
You must install a 'virtualized' windows XP over the w7 64bits.http://www.vmware.com/products/player/ (FREE)INSIDE the XP box, install the bTicino software, and all must work.Regards,James P.
Hans, welcome.Yes, You may use this but with limited functionality.1- If it is at burgar alarm bus, use an auxiliar at N4640 (MOD=Aux and AUX=NumOfAuxiliar) and a 4651/2 for recover this auxiliar and send the order to the actuator, interconnecting the two busses with F422.. 2- If the N4640 was at Automation BUS, assign the address of the actuator…[Read more]
c'e questa nuova versione per la 3500GSM?Jaume
Hi, Babs.The L4610 led is blinking?This may indicate a bad configuration.I don't know with a never firmware, but depending of Serial number, the L4610,connected at Automation bus, need a A/PL (Aka Z/N)configurators inserted (Almost PL/N)Alternatively, you may insert at 4610in automation bus:Z=1N=1MOD=ON AUX=1-7 (Timer)(and MH200 and 4651 was not…[Read more]
prova di reseteare la 3550 con il pulsante di reset…o si la bateria no e bene, le due casi il mio bus a 'latency'..Jaume
A Microcontroller with custom program, a PC with custom program…OpenWebNet protocol is Open, but you will translate to the thirty part protocol.James
It is not possible. THe DALI interface only send a 'group' order to any of the BUS.I'm agree that was better ONE BUS ONLY controlling 8 DALI adrresses…JaumeP
so, i undestand the mh200 scenario was not sending the commands to dimmers, or the orders sended from the network throught MH200 as gateway was nt sending? please clarify.At mh200 setup, TiMH200 *MUST* will detail ALL A-PL referred to dimmers and PUL.Please let me know, and I try to resolve your issues.Jaume